|Product Name:||Industrial Water Softener Machine||Usage:||Soften Water Equipment|
|Function:||Sofened Water Treatment|
Industrial Water Softener Machine , Water Softening Equipment 10 TPH
The working process of water softener, generally consists of the following steps: cyclic backwashing, salt
absorption (regeneration), slow flushing (replacement), quick rinse five process. All processes of different
softening water equipment are very close, just because the actual process or different control needs, there
may be some additional procedures. Any of the sodium ion exchange based water softening equipment is
developed based on these five processes. The automatic softener operation program:
A. operation (work)
Raw water in a certain pressure (0.2-0.6Mpa), flow rate, the body cavity by the controller, into the
containers of ion exchange resin (resin cans), resin contained in Na + and the cation in the water (Ca2 +,
magnesium 2 +, Fe2 +, etc) to exchange, which makes water of Ca2 +, magnesium 2 + ion content meet
the established requirements, to achieve the softening of hard water.
After the resins are expired, the backwash is carried out from bottom to bottom before recycling.The
purpose of reverse washing is to have two, one is through reverse washing, make the resin layer that runs
medium pressure is loosened, favorable to the resin particle and the regeneration liquid to make full
contact;The first is that the suspended solids and broken resins accumulated on the surface of the resin
are discharged with anti-wash water, so that the flow resistance of the exchanger will not become larger
C. regenerated salt
The regenerated salt solution is used to restore the original exchange capacity under certain concentration
D. replacement (slow cleaning)
In the regeneration solution into after exchanger is not involved in the regeneration of salt solution
exchange, with less than or equal to the velocity of regenerated liquid water for cleaning (slow cleaning), in
order to make full use of the role of regenerating salt liquid and reduce the wash load.
E. Washing (quick cleaning)
The aim is to remove residual waste from the resin layer and usually clean it at normal flow rate until the
water is qualified.
F. regeneration tank water flooding
The amount of salt required to regenerate the solution once more is injected into the regeneration tank
System configuration details list
The hardness of water is mainly composed of cations: Ca2 +andMg2 + ions.When containing raw water
hardness ions through the exchanger resin layer, the water of calcium and magnesium ions with sodium
ions in resin in displacement, resin absorption of calcium, magnesium ion and sodium ion in the water, so
from escaping from the exchange of water is to remove the demineralized water hardness ions.Along with
the ongoing exchange process, resin Na + all lose their ability to exchange, after it was put out at this point
you must use the sodium chloride solution for resin regeneration, the resin adsorption of Ca2 +,
magnesium 2 + displacement, resin adsorption of sodium ions, again returned to soften the exchange
10 tons softened water
cation exchange resin
Shijiazhuang Feiyue Enviromental Technology Co., Ltd is located in Shijizahuang City, built at 2013,
professional manufacturer in the field of RO pure/mineral water treatment equipment, waste water /
swimming pool water treatment equipment, bucket or bottle filling machine, wholesale agent of branded
RO Membrane, membrane housing, control valve, PP sediment filter, Ozone generator and all kinds of
accessories for water treatment equipment.
1. Own factory and engineers have experience over 20 years.
2. Own patent in RO Pure/Mineral water treatment equipment.
3. OEM & ODM available.
4. Direct manufacturer can offer the best price.
5. Already obtained worldwide partners.
6. Supply project plan, field installation, training engineer for client free of charge.
7. Products have 1 year guarantee period.
8. Lifetime after services for all our products.
Welcome to contact us.
Contact Person: yue